522 Bourbon St
VCC General Work Permit
Per attached materials stamped VCC approved 8/18/2022:
Ref code ZJDW05
Install new structural brackets on interior face of brick observation tower walls at third and fourth floor.
Repoint masonry utilizing mortar mixed and applied per the VCC standard detail sheet (attached)
Any deteriorated, cracked, or broken bricks shall be replaced to match existing in color, size, material, porosity, detail, profile and exposure. All reinstalled masonry must be properly "toothed in" to existing masonry wall, using VCC mortar formula (attached).
All mortar to be mixed using the VCC recipe (attached) with a maximum of 1 part Portland Cement, to 3 parts lime, to 9 parts sand, and enough water to form a workable mix. Prepackaged mixes are not permitted. The resulting mix should range in color from off-white to beige but should not be grey in color.
MORTAR IS NOT TO BE APPLIED OVER THE FACE OF THE BRICKS UNDER ANY CIRCUMSTANCES. VOIDS IN THE BRICK ARE NOT TO BE FILLED WITH MORTAR. BROKEN, DETERIORATED BRICKS MUST BE REPLACED WITH BRICKS MATCHING THE PREVIOUS. Doing so will result in a STOP WORK ORDER being placed on the property and violation case will be opened on the property.